This sealing combination is suitable for fire engineered designs where quantifiable medium temperature smoke leakage rates are required.
This system is tested in accordance with AS1530 Part 7 and complies with the requirements of AS6905.
Medium Temperature Test Results (Corrected to STP*)
|Door Configuration / Pressure||Exposure Temp||Door Perimeter Tested||Leakage Rate (m3h) corrected to STP conditions @ a Pressure Differential of|
|Opening Towards Positive Pressure (fire side)||Medium (200ºC)||Entire Perimeter||< 2||2||3|
|Opening Towards Positive Pressure (fire side)||BCA Spec C3.4 Medium (200ºC) > 30 minutes||Entire Perimeter||< 2||3||5|
Note: The medium test with exposure times greater than 30 minutes is consistent with the BCA requirements of Specification C3.4 which requires doorsets to be resistant to smoke at 200ºC for 30 minutes.
Register To Download
Please register your details to download your requested file.
For more information and copies of relevant certificates contact Kilargo