Fire Rated Plasterboard Two Ply Ceiling
This IFD System using a IFD-CE4 Fire Rated Ceiling box is suitable use with Three Way Fan / Heat / Light units where a 90 min fire rating and 90 min RISF installation is required. It is suitable for residential or multi residential installations situation including apartments, hotels, motels & aged care facilities, where containment of fire / hot smoke is required.
To comply with the Building Code of Australia and referenced standard AS1668.1, Kilargo IFD series IFD’s are fully fire tested to AS1530.4 and air leakage tested in accordance with AS1682.1
Related Standards and Codes: AS1668.1 / AS1530.4 / AS1682.1 / AS1682.2 / AS1851.6
Kilargo has conducted an extensive testing program of IFD’S at CSIRO, Exova Warrington and BRANZ registered test authorities.
Approved Product Sizes:
Nominal 300 x 300mm or 400 x 400mm ceiling opening size.
Register To Download
Please register your details to download your requested file.
For more information and copies of relevant certificates contact Kilargo